CROSS Safety Report
Collapse of brickwork cladding
This report is over 2 years old
The external leaf of a brickwork pier at first floor level fell down onto the playground of a school adjacent to the main entrance door.
Key Learning Outcomes
For building owners and managers:
Regular inspections and maintenance can help keep a structure safe and identify any obvious safety issues that may need to be addressed
Be aware that safety critical defects may be hidden behind linings
Find out more about the Full Report
The Full Report below has been submitted to CROSS and describes the reporter’s experience. The text has been edited for clarity and to ensure anonymity and confidentiality by removing any identifiable details. If you would like to know more about our secure reporting process or submit a report yourself, please visit the reporting to CROSS-UK page.
The external leaf of a brickwork pier at first floor level fell down onto the playground of a school adjacent to the main entrance door. Fortunately, there were no casualties. The reporter believes that the structure is a concrete encased steel frame. Bricks on end had been used on either side of a column between windows to form a cavity and an external skin built without provision for tying back to the main frame (Figure 1).
The school was closed for an initial period of a week whilst investigations were carried out on the rest of the elevation. The brickwork cladding was removed and replaced with an alternative material. The reporter’s firm has advised the local authority in case there are other schools of similar construction in the same ownership.
Expert Panel Comments
Find out more about the Expert Panels
Expert Panels comment on the reports we receive. They use their experience to help you understand what can be learned from the reports. If you would like to know more, please visit the CROSS-UK Expert Panels page.
As with many other reports of masonry falls from buildings it is fortunate that there was nobody underneath at the time of collapse. The SCOTCROSS project which gathered data over a two year period up to August 2007 had 1,200 reports of material falling, or in danger of falling, from old buildings. In 12 cases passers by were injured.
A full report on the project was published by the Scottish Building Standards Division. There is a risk to people from falls such as the one given above, and they are usually due to combinations of poor construction, poor maintenance, and weathering. The most significant failures are those where there is a pattern and hence further falls can be expected if nothing is done.
The Scottish investigation may be extended to other parts of the UK but meanwhile CROSS welcomes reports of falling, or dangerous and about to fall, materials. So far as new construction is concerned this is perhaps a timely reminder that good building practice requires the ability to see how all items are restrained and retained within buildings, and that construction industry professionals should be proficient at good detailing.
It is also a reminder to school authorities and school governors of the importance of regular condition surveys to detect defects before they become dangerous.
Submit a report
Your report will make a difference. It will help to create positive change and improve safety.
Our secure and confidential safety reporting system gives professionals the opportunity to share their experiences to help others.
No feedback has yet been published for this page.