CROSS Safety Report
Flaws with partial encasements around steel columns
This report is over 2 years old
A structural assessment found that steel columns encased in concrete to mid-storey height were heavily corroded directly above the top of the encasements.
Key Learning Outcomes
For civil and structural design engineers:
Adequate corrosion protection for the given environment should be provided to all construction elements to ensure they perform as expected
Good detailing is also a prerequisite for longevity and the safety of a structure
For building owners and managers:
Regular inspections and maintenance can help keep a structure safe and to detect any obvious maintenance issues
Find out more about the Full Report
The Full Report below has been submitted to CROSS and describes the reporter’s experience. The text has been edited for clarity and to ensure anonymity and confidentiality by removing any identifiable details. If you would like to know more about our secure reporting process or submit a report yourself, please visit the reporting to CROSS-UK page.
A structural assessment was carried out on a 40 year old steel framed structure in a pharmaceutical plant. Concrete encasements, with flat tops, had been formed up to mid-storey height around steel columns. Heavy corrosion was apparent at mid-storey height i.e. directly above the top of the encasements.
The encasements were cracked below mid-story height and upon removal of the concrete, it was found that the thickness of the steel columns were substantially reduced. Vapours and liquids had gathered on the flat surface and corroded the steel overtime. The absence of maintenance and the humid atmosphere (high temperature process area) aided the rate of corrosion.
To avoid this problem, the reporter recommends the following:
Form a chamfer around the top of concrete encasements
Avoid stopping the encasements at mid-storey height
Galvanise steelwork in corrosive environments
Ensure that the steel to concrete joint is adequate to mitigate liquid/moisture ingress
Submit a report
Your report will make a difference. It will help to create positive change and improve safety.
Our secure and confidential safety reporting system gives professionals the opportunity to share their experiences to help others.
No feedback has yet been published for this page.
Expert Panel Comments
Expert Panels comment on the reports we receive. They use their experience to help you understand what can be learned from the reports. If you would like to know more, please visit the CROSS-UK Expert Panels page.
Corrosion on older assets in harsh industrial environments is commonplace, and potentially critical to stability and hence safe use. This is a legacy of an era when inadequate attention was given to life-long performance, often coupled with less than adequate inspections over its life. Good detailing is a prerequisite for longevity and the safety of a structure only exists at a point in time related to the as-built condition.
Good detailing is a prerequisite for longevity and the safety of a structure only exists at a point in time related to the as-built condition
In all refurbishment projects, a key part of the work should be to fully assess the structure’s state as far as is possible. Cracking should be investigated as previous repairs to the concrete may not have addressed any underlying section loss. Such investigations should also consider the possibility that the encasement is providing an unintended load path and therefore removal may impact the element capacity.
A building being used as a workplace should be capable of supporting all foreseeable loads imposed upon it (Workplace (Health, Safety and Welfare) Regulations 1992). Depending upon the nature of the workplace, a foreseeable load might include accidental impact from a forklift truck.
Whilst this might be the precise reason for encasing the columns, given the reporter’s findings, it may be appropriate to implement additional measures that remove or reduce the risk of accidental impact.
The reporter’s recommendations are very sensible and if adopted as a matter of course would improve the life of new constructions.