CROSS Safety Report
Plasterwork ceiling partial collapse at railway station
This report is over 2 years old
A section of a ceiling cornice, plasterboard panel and lighting collapsed at a railway station landing on the floor.
Key Learning Outcomes
For asset owners and managers:
Regular inspections and maintenance can help keep structures and elements safe and identify any obvious safety issues
The asbestos management plan should be made available to all contractors carrying out works where there is a risk of asbestos being present
For construction professionals:
Quality management and competent supervision on site can help to ensure that the structure is built in accordance with the design
If there are no asbestos records or management plan on file an asbestos survey should be carried out by a competent contractor prior to any works commencing on site
Find out more about the Full Report
The Full Report below has been submitted to CROSS and describes the reporter’s experience. The text has been edited for clarity and to ensure anonymity and confidentiality by removing any identifiable details. If you would like to know more about our secure reporting process or submit a report yourself, please visit the reporting to CROSS-UK page.
One morning, a railway employee opened the station as normal and saw a section of the cornice, plasterboard roof and lighting on the floor. The entrance to the ticket office was closed until the debris was cleared and the roof could be made safe. Electricians made the electrical connections safe and a full crash deck was installed just below roof level to ensure the station can be operated and safe access made to the ceiling.
Initial investigations show that the light fixtures were not adequately retained and with only rawlplugs into the plaster. Also, no evidence of damp in this area was witnessed previously. The owner confirmed all maintenance to the guttering has been completed to allow free-flowing drainage.
Contractor awareness heightened as they should have suspected asbestos before works commenced on site. The contractor concerned was briefed on the correct procedures according to the asbestos management plan and the project team completed their own investigation to ensure this does not happen again. This is a busy station, and the impact could have caused an injury during a busy time. Fortunately, it was at night, so no injuries occurred.
Expert Panel Comments
Find out more about the Expert Panels
Expert Panels comment on the reports we receive. They use their experience to help you understand what can be learned from the reports. If you would like to know more, please visit the CROSS-UK Expert Panels page.
There are no Expert Panel comments on this report. The Expert Panels are only asked to comment on selected reports. These are normally reports where there is an opportunity for them to help you understand what can be learned from the report.
Submit a report
Your report will make a difference. It will help to create positive change and improve safety.
Our secure and confidential safety reporting system gives professionals the opportunity to share their experiences to help others.
No feedback has yet been published for this page.