CROSS Safety Report
This report is over 2 years old
A reporter has come across a situation where during grouting of the ducts in a slab, patches of concrete as big as 0.5m x 1m and 30mm thick fell on to the ground creating a safety hazard.
Key Learning Outcomes
For the construction team:
Post-tensioning and pre-stressing operations should be carried out by people who have the relevant training and are competent to do so
Quality control and competent supervision on site can help to ensure that the structure is built in accordance with the design
Regular toolbox talks with work crews are a good way of highlighting any risks associated with work activities
Find out more about the Full Report
Our secure and confidential safety reporting system gives professionals the opportunity to share their experiences to help others. If you would like to know more, please visit the reporting to CROSS-UK page.
Pre-stressing in concrete has been used in bridges and heavy civil structures for many years and more recently in buildings. A reporter has come across a situation where during grouting of the ducts in a slab, patches of concrete as big as 0.5m x 1m and 30mm thick fell on to the ground creating a safety hazard (Figure 1). Investigation showed that the main reasons for falling patches of concrete were combinations of the following:
During grout the pressure was not monitored at the delivery end and entry end into the duct and higher pressures than normal were used
The grout was expanding very quickly - more than that which was specified
The ambient temperature was too low during grouting
Water found its way into the lowest points of the duct during rain and eventually froze resulting in partial ice expansion
Expert Panel Comments
Find out more about the Expert Panels
Expert Panels comment on the reports we receive. They use their experience to help you understand what can be learned from the reports. If you would like to know more, please visit the CROSS-UK Expert Panels page.
Grouting of pre-stressing ducts requires careful workmanship and supervision. Recent investigations have revealed the likelihood of a lack of properly grouted ducts in some buildings. One method of minimising the risks is to ensure that post tensioning installation is only carried out by properly trained teams, for example those certified for PT installation through the UK CARES certification Scheme.
It should be noted that point 4 above (water ingress and freezing) can occur in completed structures where grouting has not been properly executed. Guidance on procedures and techniques is given on the CARES website. Reference is made to the need for project specific reviews and advice is given for new structures.
Share your knowledge
Your report will make a difference. It will help to create positive change and improve safety.
Our secure and confidential safety reporting system gives professionals the opportunity to share their experiences to help others.
No feedback has yet been published for this page.